Tootallsteve Posted June 4, 2022 Share Posted June 4, 2022 I'm setting up a 6 K with 220 grid tie and out putting to a new panel. I have all my circuits in the new panel and have it ran to a breaker to the old panel temporally. When I hook up the inverter disconnect the 2 hot leads and run them through the 6K is it OK to leave the neutral between the panels connected? Thanks Steve Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.